INTENDED USE
Ideal one-for-one replacement of conventional HID and fluorescent high bay systems. Applications include warehousing, manufacturing, gymnasiums, and other large indoor spaces with mounting heights up to 60'. Certain airborne contaminants can diminish integrity of acrylic.  Click here for Acrylic Environmental Compatibility table for suitable uses.

CONSTRUCTION
Lightweight aluminum heat sink designed to perform in ambient temperatures up to 55 ° C with lumen droop less than fluorescent due to precision thermal engineering for maximum naturally convective cooling. Structural elements such as the channel and end caps are fabricated from steel for maximum rigidity. Hard-tooled reflectors, utilizing reflective Alanod® MIRO-5® aluminum, for precise and repeatable photometry. Semi-diffuse lens optional to provide glare control – may be inverted for gloss or matte side down. Wireguard attachment points provided.

OPTICS
Narrow and wide distributions available to meet both horizontal and vertical light level requirements. Reflectors feature precision-formed optics utilizing reflective Alanod® MIRO-5® aluminum to achieve narrow distribution and white polyester powder coat to achieve wide distri bution. Semi-diffuse lens optional to provide glare control and LED protection.

ELECTRICAL
L95 at 60,000 hours (only 5% loss) with a predicted life of more than 100,000 hours. Utilizes a 90°C case temperature driver for maximum life at high temperatures. 0.90 power factor and 10kA/10kV level of surge protection is standard.  Available as 120-277V or 347-480V input. 0-10V dimming standard for a dimming range of 100% to 10%; dimming source current is 150 microA.

WIRELESS NETWORKING
Point™ Wireless technology creates a mesh network to ensure communication between fixtures, sensors and wall stations facility-wide. This option provides superior lighting management capabilities including granular control, configuration and custom grouping for increased energy savings.

INSTALLATION
Suitable for suspension by chain, cable, surface-mounting bracket, hook monopoint or single (pendant) monopoint. Surface mounting not recommended without optional surface mounting bracket. To maintain high ambient listing, fixture should be mounted at a minimum plenum height of 24".  

LISTINGS
CSA certified to US and Canadian safety standards. Damp location listed. Suitable for ambient temperatures from -40°F (-40°C) to 131°F (55°C) when suspended 24" from ceiling. Patent pending. DesignLights Consortium® (DLC) qualified product. Not all versions of this product may be DLC qualified. Please check the DLC Qualified Products List at www.designlights.org/QPL to confirm which versions are qualified.
  
WARRANTY
5-year limited warranty. Complete warranty terms located at  www.acuitybrands.com/CustomerResources/Terms_and_conditions.aspx Note
Actual performance may differ as a result of end-user environment and application. All values are design or typical values, measured under laboratory conditions at 25 °C. Specifications subject to change without notice.