An adjustable multi-lamp recessed fixture with available 0.75” (19mm) trim flange, trimless for mud-in drywall and truly trimless for hard surface and special ceiling installations. Combolight LED is offered in various LED module configurations from One to Six (1-6) LED Modules.

Applicable for new construction applications in IC and non-IC conditions.

For non-IC applications, insulation must be kept 3” (76mm) from all sides and at least 1”(25mm) above the housing. For use in insulated ceiling applications, housing may be covered on all sides with insulation material.

 Housing
Housing and junction box are constructed from CRS. Trim & trimless meshplate assembly are all steel construction.

System Protection / Electrical
Thermal protection provided to guard against overheating.

Junction Box is UL listed for through branch wiring, 6 #12 90º C conductors or 60º C for end of run. Electrical accessible through ceiling opening. Integral LED drivers are mounted in a separate metal enclosure box attached to the housing with 18” flexible conduit. Includes a separated wiring compartment with knockouts and a maintenance door.

 LED Modules
1, 2, 3, 4, 5 or 6 LED modules mounted in adjustable double gimbals with field changable optics. 40° x 40° locking lamp adjustment. Spacer rings are available for additional media.

Passive cooling achieves L70 at 50,000 hours. Various lumen ranges from 613-2432 lumens per module as well as minimum CRI from 90-95 dependent on modules choice.

Trim / Trimless / Special Ceiling
Trimmed housing utilizes a removable trim sleeve to provide a 0.75” flange around the ceiling aperture. Trimless housing includes perforated meshplate for trimless installation in drywall/ plaster ceilings by allowing the ceiling’s mudding compound to be applied right up to the edge of the fixture opening. Includes a beveled “knifeedge” lip to ensure a clean edge. Special Ceiling applications feature a welded collar for hard surface applications.

Compliance
Type Non-IC inherently protected, insulation must be kept 3” (76mm) from all sides and at least 1”(25mm) above the housing.

cULus listed for damp locations.

Type IC inherently protected, suitable for direct contact with insulation and cULus listed for damp locations. Contains no mercury or lead and RoHS compliant. Photometric testing in accordance with IES LM-79-08.

Lumen maintenance projections in accordance with IES LM-80-08 and TM-21-11.

Warranty
5 year warranty