Beautifully constructed with high quality architectural grade die-cast aluminum, the MB-LED accent series offers long-lasting and energy-saving LED lighting. Guaranteed color consistency and control creates optimal performance with every fixture. Precision optics are uniquely constructed to intentionally regress the position of the LED array. This provides the best possible shielding and glare control while delivering crisp, bright light. Multiple accessories are also available for further control.

LED LIGHT ENGINE.

2700K, 3000K, 3500K and 4100K 82 CRI
2700K and 3000K 92 CRI (R9 Value = 59)
3 Step MacAdam (3 SDCM)
LED mounted to die-cast / extruded aluminum heat sink
50,000 hours average rated life at 70% output.

OPTICS.

17° Spot, 30° Narrow Flood, and 55° Wide Flood.

ELECTRICAL SYSTEM.

120V-277V 50/60Hz input
Class 2 power supply
Over voltage, over current and short circuit protection
Auto recovery MTBF > 100,000 hours This product complies with IEEE C62.41 for surge endurance up to 2.5KV. Additional surge protection recommended. Damage from power surge is not covered by warranty.

DIMMING.

Must specify -DIM for ELV Dimming
(ELV) reverse phase control dimmers. 120V only
Dimmable 100 - 10%.

TRACK COMPATIBILITY
Track luminaire is designed for use with the following track systems
Single Circuit/Single Neutral 120V
Two Circuit/Single Neutral 120V
Pro-Series Two Circuit / Two Neutral 120V
Pro-Series Two Circuit / Two Neutral 277V; J-Type & L-Type Adapter are for Single Circuit (Consult factory for Two Circuit).

LISTING/WARRANTY
ETL Listed to US and Canadian standards for dry locations
10-Year Intense LED Limited Warranty
ENERGY STAR® Qualified