Small aperture led downlight fully adjustable with element’s unique patented high-low lamp positioning. The innovative design allows the LED to be positioned closer to the aperture for maximum light output and efficiency or higher to minimize glare and flash on the trim. Additional adjustability allows for tool-free hot aiming including 0°- 40° tilt and 361° rotation to eliminate dead spots. All aiming functions are lockable. Also available as a fixed downlight. Wood ceiling option allows for a smooth, flangeless appearance using any flangeless trim.

LAMPING & OPTICS
 High Output
- 1500 / 1200 net lumens at 3000K (80 CRI / 90 CRI) - 83 / 67 net lumens per watt at 3000K (80 CRI / 90 CRI) Low Output
- 1000 / 800 net lumens at 3000K (80 CRI / 90 CRI) - 83 / 67 net lumens per watt at 3000K (80 CRI / 90 CRI)  CA Title 24 Compliant with 90 CRI versions  2700K, 3000K, 3500K with 3-step color binning  Field-changeable optic
15°, 25°, 40° (CBCP
5618, 3856, 1575 respectively). Accepts two optical controls and an optional trim mounted lens POWER / POWER SUPPLY
 High Output
18 watts. Low Output
12 watts  Constant current driver with +.9 power factor and +80% efficiency  Dimmable with ELV or incandescent dimmer to 2%-15% depending on dimmer; see ELEMENT-Lighting.com for compatibility  Optional Lutron Hi-Lume™ driver – HL2W / PWM – Two wire low-voltage electronic dimming – HL3W / ECO – Three wire dimming of Lutron Eco-System®  Optional 0-10V dimming  Consult Quotes Dept for alternate or custom driver selections TRIMS  Die cast aluminum, flanged or flangeless ceiling appearance  Lensed and shower aperture includes Solite™ soft focus lens  White can be field painted to match adjacent finishes. Accommodates up to 2.5" drywall ceiling thickness, depending on trim  Wood ceiling option accommodates variable ceiling thickness.

Consult instructions for details.

HOUSING
 IC / Non-IC / Chicago Plenum
11.5" x 17.5" x 6"  Emergency Battery (IC / Non-IC / Chicago Plenum)
11.5" x 20.5" x 6.6"  Emergency Housing
Adjustable LED housing with integrated emergency battery back-up. Provides 1000 net lumens for up to 110 minutes in emergency mode. Ships complete with a remote mounted test switch and indicator light.

 Constructed of heavy gauge cold rolled steel with durable matte black powder coat finish  3-7/8" ceiling opening, offset  Includes integral junction box approved for branch circuit through wiring  ETL listed. Damp listed. Shower version wet listed.