ChromaSure

Color consistency resulting in a 2-step MacAdam ellipse across the entire ID+ product line.

Field adjustability of ceiling thickness from 0.5" - 2.5".

Shallow housing.50 degree cutoff to light source and its image.

Selection of dimming drivers available.

Right Light

Standard delivered lumen outputs 1000, 1500, 2000, 2500 and 3000.



HOUSING SPECIFICATIONS



CONSTRUCTION

Thermally protected housing for new construction applications. Insulation to be kept 3" away from housing. Butterfly brackets allow mounting to ½ emt. Order bar hangers as an accessory. Die-cast aluminum heat sink designed for maximum thermal dissipation. Die-formed housing and integral junction box with (7) 1?2" pry outs. UL & cUL listed for (6) #14 AWG (3 in, 3 out) 90°C conductors and feed through–branch wiring. Accommodates ceiling thicknesses up to 0.5" standard, field adjustable up to 2.5" thickness. For thicker ceiling consult factory. Fixture will not exceed 5 lb.





ELECTRICAL

Choice of constant current dimming drivers. Power factor > .9 typical.



Emergency

Emergency Battery Pack

Bodine BSL17C–C2. Emergency output —7W for 90 minu



LABELS

UL and cUL listed. Wet Location listed, indoor use only.



LUMEN MAINTENANCE

Reported

L70 at >63,000 hours Derived from EPA TM-21 calculator Warranty

LED System rated for operation in ambient environments up to 25°C. 5 year limited warranty.



TRIM & LED SPECIFICATIONS LED SYSTEM

Proprietary array incorporates premium LEDs on a robust platform. May be specified in 2700K, 3000K, 3500K or 4000K, CRI>80. Color accuracy within 2 SDCM. Aluminum heat sink provides appropriate thermal management.





AESTHETICS



Die–formed aluminum reflector ensures glare free optics. Reflector attaches to die-cast, seamless flange and may be removed for field painting.Torsion springs pull trim tight to theceiling with no visible fasteners within the trim.



OPTICS

55-degree cut–off to light source and its image.