Low brightness 4-1/2” aperture LED adjustable accent fixture with choice of distribution. Adjustment mechanism enables the LED beam to pivot through the center of the aperture at the ceiling line, allowing maximum light output with no flashback. Offered with flat cut, adjustable accent, pinhole, and lensed wall wash trims.







Lower Reflector:



Spun 0.050” aluminum. Available in a variety of Alzak® and painted finishes. Two torsion springs pull trim tight to ceiling. Truncated adjustable cut cone allows for full tilt range and flexibility. Lensed wall wash provides even illumination on vertical surfaces. Pinhole includes black oculus to control glare.







Upper Reflector:



Field interchangeable optics in 15º, 25º or 35º provides smooth beam without color separation. Media holder fits onto upper reflector and holds up to two lens media.







Trim Ring:



Self flanged or white polymer trim ring.







Adjustment MechanismStable aiming and locking mechanism allows smooth 362° rotation and 40° elevation adjustment. Aiming scale enables consistent setting across multiple fixtures.







Housing:



One piece die cast 1-1/4” deep collar.18 gauge CRS housing is painted matte black to eliminate stray light. Housing is toolless top accessible.







Universal Mounting BracketAccepts 1/2” EMT, C Channel, T bar fasteners and hanger bars. Provides 5” total adjustment.







Thermal:



Aluminum heat sink conducts heat away from the LED module for optimal performance and longer life.







LED:



LED system contains a plurality of high brightness white LED’s combined with a high reflectance upper reflector producing even distribution with no pixilation. Rated for 50,000 hours at 70% lumen maintenance. Auto resetting, thermally protected, LED’s are turned off when safe operating temperatures are exceeded. Color variation within 3-step MacAdam ellipses.







Driver:



Combination 120-277V 0-10V or 120V trailing edge phase cut driver provides flicker free dimming from 100% to 10%. Optional 1% 0-10V, Fifth Light, or DMX. Driver can be serviced from above or through the aperture.







Code ComplianceThermally protected and cULus listed for damp locations with flat cut, pinhole or angle cut and wet location covered ceiling with lensed or lensed wall wash. Optional City of Chicago environmental air (CCEA) marking for plenum applications. EMI/RFI emissions per FCC 47CFR Part 18 Class B consumer limits. 2800 lumen Non-IC rated - Insulation must be kept 3” from top and sides of housing. IC rated up to 1800 lumen. RoHS Compliant. 2800 lumen and above spacing and must follow spacing requirements. Photometric testing completed in accordance with IES LM 79 standards. LED life testing completed in accordance with LM 80 standards.







Warranty:



5 year warranty.