Technical Specifications



Distribution Types

Type V-Narrow or V-Square roadway distributions available.  UV-stabilized, high-impact resistant injection-molded clear textured 100% DR acrylic or polycarbonate tertiary lens.


Electrical

Serviceable high-brightness LED array.  See Ordering Information for color temperature and CRI options.  70 CRI minimum.  120-277 VAC, 347VAC and 480VAC 50/60Hz single-phase input; constant-current dimming driver; 0.90 PF. Minimum 90% electrical efficiency.  0-10V dimming protocol with 0-100% range, 0.6mA source current.  Replaceable surge suppressor rated to 20kA/kV per IEEE/ANSI C62.41 Cat. A.  EMC compliant with FCC 47 CFR Part 15, Class B. Passes IEC 61000-4-4 EFT and IEC 61000-4-5 (Class 4) surge evaluation.



Housing

Marine-grade die-cast aluminum and UV-stabilized polycarbonate construction.  Standard TGIC polyester power coat finish on aluminum components with five-step pre-treatment to withstand 1,000 hour salt spray test per ASTM B117.  See Ordering Information for available finishes. Closed-cell silicone gasketing seals all housing component interfaces.  Die-cut closed-cell neoprene self-adhesive gasket seals housing to mounting surface (DTS).




Listings

Luminaire is certified to UL Standards by Intertek Testing Laboratory for Wet Location.  IP65 rating per IEC 60598.  Suitable for installation into -40°C to 40°C ambient environments, unless otherwise noted. Product listed on DesignLights Consortium® Qualified Product List. Check the latest version here for listed configuration details. 



Lumen DatA

TD17 Lumen Data 



Mounting

Direct-to-surface (DTS) mounting over recessed junction box, Trunnion Mount (TK) or pendant-mounted (PM) via ¾" rigid sealed conduit.  See Ordering Information for selection. Housing access secured via tamper-resistant Torx™ fasteners.



Patent

Multiple U.S. Patents issued and pending.



Photometrics

Photometry tested to the IESNA LM-79-08 standard by an ILAC/ISO17025 accredited laboratory.  For photometric data, please go to www.kenall.com.



TekLink TL1000/2000

An adaptive lighting control system with wired or wireless communication between system nodes.  In addition to occupancy detection and daylight harvesting, TL1000 and TL2000 feature advanced scheduling and energy management capabilities with cloud-based management of system settings, reporting and notifications.  Meets CA Title 24-2013 and ASHRAE 90.1-2013 requirements.



TekLink TL50

An independent lighting control system integral to the luminaire, featuring its own occupancy sensor, daylight harvesting and adjustable time-out/dimming settings.  



Warranty

Limited ten (10) year warranty.  Peace of Mind Guarantee™ when ordered and installed with direct-to-surface (DTS) mounting and polycarbonate lens (TP).