<b>Description</b>

Recessed 1.5” directional pinhole luminaire utilizing a LED array.
Housing is air tight and suitable for 2x8 residential or commercial constructions. Insulation must be kept 3"" from top and sides on housing. Housing platform + primary reflector + optical element combination supports various distributions and reflector types providing design flexibility. Use where excellent light control and low aperture brightness are demanded.

<b>Frame</b>
Galvanized steel plaster frame with integral bar hanger receivers.

Setscrews provide positive horizontal locking. Integral gun sights facilitate the use of guide strings or laser lines.

Shipped with overspray protector installed.

<b>Housing</b>
Steel housing painted matte black for visually dark interior. Removable access panels allow splice inspection and service of all electrical components including LED module and driver from below the ceiling thru the aperture. Removable hinged top allow top access. All fasteners are captive.

<b>Bar Hangers</b> 
Captive preinstalled bar hangers adjust from 8-1/2” to 24” wide; pass thru feature allows shortening without removal. Captive nail penetrates standard and engineered lumber.

Mounting flange levels platform with ceiling. Integral clip attached directly to tee-bar.

Universal Mounting Bracket 
Accepts 1/2” EMT, C channel and bar hangers and adjusts 3” vertically from above the ceiling.

<b>Gaskets</b> 
Closed cell gaskets achieve restrictive airflow requirements without additional caulking.

<b>Adjustment Mechanism</b> 
Dynamic aiming rotates 365°, tilts 45° and locks in position. Angle markings assist in repeatable settings.

Translating center beam optics aligns axis of primary reflector with aperture from nadir to 45°.

<b>LED Module</b> 
Field replaceable module utilizes Cree® MT-G2 LED array and conforms to Zhaga standards for interchangeability.

Proximity phosphors over chip on board LEDs provide a uniform source with high efficiency and no pixilation.

Color accuracy within 2 SDCM and optional 90 CRI provides excellent color. Passive cooling achieves L70 at 40,000 hours.

<b>Primary Optic</b> 
Borosilicate glass segmented optic with > 95% reflective multi-layer hard coating delivers a highly efficient and uniform beam. Various distributions are available and can be interchanged without tools. Elastomeric glare shield accepts theatrical color filters and diffusion films.

<b>Media</b> 
Optional media holder accepts one or two 2 inch [50mm] diameter L series color filters or beam modifying lens.

Order media holder, color filters and lens separately.

<b>Splay</b> 
Die cast aluminum splay with pinhole aperture and black oculus for glare control. Oculus can be removed to facilitate painting or to create 1.75” aperture (E3PINLARGE). Can be installed flush mount with optional flush mount collar accessory.

<b>Trim Retention</b>
Retained with two torsion springs holding the flange tightly to the finished ceiling surface and accommodates ceiling thickness from 1/2” - 1” thick. Use optional plaster lip extender for ceilings up to 2"" thick.

<b>Junction Box</b> 
(6) 1/2” and (2) 3/4” trade size pry outs positioned to allow straight conduit runs.

<b>Driver</b> 
Integral constant current driver provides noise free operation.

Continuous, flicker-free 1% dimming, available with 2 or 3 wire phase cutand EcoSystem/DALI digital control interfaces. The DALI option is Fifth Light compatible.

<b>Compliance</b> 
Type Non-IC inherently protected and cULus listed for damp locations.

Insulation must be kept 3"" from top and sides on housing. Restrictive airflow per ASTM-E283. EMI/RFI emissions per FCC 47CFR Part 18 consumer limits. Contains no mercury or lead and RoHS compliant.

Photometric testing in accordance with IES LM-79-08. Lumen maintenance projections in accordance with IES LM-80-08 and TM-21-11. Meets California Title 24 residential fixture program and listed on appliance database. Energy Star listed. Zhaga compliant. Meets EMI/RFI emission per FCC 47CFR Part 18 consumer limits at 120V input. Lighting Facts Labeled.

<b>Warranty</b> 
5 year warranty"