Kim Lighting introduces the ArcheType X Site/Area Luminaire. LEAR Modules allow these luminaires to take on tasks previously accomplished by ground-mounted sign lighting or landscape level products. Vertical illuminance without obtrusive glare or wasteful spill light is created by simply aiming the LEAR Module toward the target.

FEATURES Certifi cations Independently aim able LEAR™ modules 355° horizontal and 70° vertical module adjustment Wide range of drive currents available Design software interface for custom Type X distribution creation Traditional NEMA distributions available IP66 sealed optical chamber Housing
Low copper aluminum alloy die-casting is designed as one-piece and has external cooling ribs.

Solid, cast aluminum, wall creates a thermal barrier between the optical and electrical compartments.

A molded silicone gasket throughout insures the sealing between the two compartments and provides ingress protection.

Housing is designed with integral LED module “turrets” utilized for both thermal transfer and for securing the location of each LEAR™ Optical Module. The turrets are spaced in rows of 3 X 3 and are designed to optimize photometric performance for standard and custom Type X distributions.

IP66 certifi ed to protect the optical chamber from dust and water ingress.

Lens Frame
One-piece low copper aluminum alloy die-cast is secured to housing with two toolless latches.

Neighbor Friendly Optic Optional integrated Neighbor Friendly Optic on each LED module to completely control unwanted backlight. Most effective with Type III and IV distibutions.

Lens One-piece fl at glass lens slips into reveal. Extra silicone gasketing is provided to retain a clear optical compartment. CAUTION
Use only when vandalism is anticipated to be high.

Type X LEAR™ Optical Module
Turret alignment and thermal transfer design allows for freedom of adjustability and precise aiming of the LEAR LED array.

Custom, factory adjusted, distributions using IES fi les created using design software.

Optimized standard distribution.

3000K, 4000K, 5000K standard CCT. Amber and other custom color temperatures available.

Each LEAR module provides 355° of rotation and 70° of tilt independent of the housing.

Type X LEAR modules are IP66 rated and utilize six high output LEDs positioned beneath a precise, high purity molded acrylic prism.

Targeted optics minimize pixilation concerns and provide outstanding performance, uniformity and glare control.

Electrical Components
Standard programmable driver allows for programmable drive current settings ranging from 350mA to 700mA.

Electrical components are stategically located in the driver gear compartment with a molded silicon grommet seal to provide separation from the optical chamber.

Maximum lightning surge current 20KA with thermally protected varistor technology. Surge suppression is series circuited preventing total fi xture failure.

Open circuit fault will turn off the luminaire in order to protect the sensitive electronics and acts as a signal for maintenance.

Programmable Driver is rated for -40°F starting.

"Thermal Shield”, primary side, thermister provides protection for the sustainable life of LEAR modules and electronic components.

Dimming range from 10% to 100% through the use of the standard 0-10V interface on the programmable driver.

Modular wiring harness in the service area provides user access to the dimming circuitry.

Dimming circuitry compatible with 0-10V, user-defined, control devices.

Optional factory programmed dimming profile.

Support Arm
? Die-cast, low copper aluminum alloy, with splice access cover.

? D ie-cast pole adaptor and an internal reinforcing plate are provided with a wire strain relief.

The arm adapter is square or circular cut for specifi ed pole size and shape.

For fi eld wire connections, a terminal block is mounted in the arm cavity and accessible behind the splice access cover. The block accepts #14 to #8 wire sizes and is factory prewired to the electrical module's quick-disconnect plug inside the electrical compartment.

Optional Slip-Fitter
Internally accessible slip-fi tter attaches to a 1-1/4” to 2-3/8” tenon and allows hands-free wiring and maintenance.

Optional Wall Mount
Optional, cast aluminum mounting plate attaches to a wall over a junction box and the speed mount is bolted to the cover plate. To complete the wiring, the luminaire assembly slides over the mounting plate.

Fusing
SF for 120, 277, and 347 Line volts DF for 208, 240, and 480 Line volts Hight temperature fuse holders factory installed inside the fi xture housing.

Fuse is included.

Finish
Fade and abrasion resistant, electrostatically applied, thermally cured, triglycidal isocyanurate (TGIC) polyester powdercoat.

Standard colors include (BL) Black, (DB) Dark Bronze, (PS) Platinum Silver, (LG) Light Gray, (TT) Titanium, (WH) White, and (CC) Custom Color (Include RAL#).

Certifi cations and Listings
UL 1598 Standard for Luminaires.

UL 8750 Standard for Safety for Light Emitting Diode (LED) Equipment for use in Lighting Products.

CSA C22.2#250.0 Luminaires.

ANSI C136.31-2010 4G Vibration tested and compliant.

RoHS compliant.

IP66 certifi ed.

CAUTION
Fixtures must be grounded in accordance with national, state and/or local electrical codes.

Failure to do so may result in serious personal injury.

WARRANTY
For full warranty see
http://www.

hubbelllighting.com/resources/warranty