Technical Specifications


Electrical

Serviceable high-brightness ANSI 4000K, 5000K and 5700K white LED array.  70 CRI min.  See Options for higher CRI availability.  120-277 VAC, 347 VAC and 480 VAC 50/60Hz single-phase input; constant-current dimming driver; 0.90 PF.  Minimum 90% electrical efficiency. 0-10V dimming protocol with 0-100% dimming range, 1.2mA source current.  Replaceable surge suppressor rated to 20kA/kV per IEEE/ANSI C62.41 Cat. A.  EMC compliant with FCC 47 CFR Part 15, Class B.  Passes IEC 61000-4-4 EFT and IEC 61000-4-5 (Class 4)surge evaluation.



Housing

Marine grade die-cast aluminum. Integral heatsink with concealed convection fins. TGIC polyester powder coat finish with 5-step pre-treatment. Salt spray test: 1,000 hours. See Ordering Information for available finishes. Closed-cell silicone gasketing at all housing interfaces. 



Listings

Luminaire is certified to UL Standards 1598 and 8750 by Intertek Testing Laboratory for Wet Location. IP65 per IEC 60598. IESNA-designated full cut-off.  IDA-Approved™ Dark-Sky Friendly Fixture. Luminaire is 2G tested for vibration per  ANSI C136.31. 


Lumen Data

TPD23 Lumen Data 



Mounting

Compatible with 3"-6" square steel or aluminum poles, 3"-6" tapered and non-tapered round steel or aluminum poles. Poles by others. All structural hardware 304 stainless steel, or zinc plated steel Grade 8.



Note

-40ºC and 40ºC ambient temperature rated unless otherwise noted.  (See photometric data for light output reductions at higher ambient temperatures). 



Optics

Type II, III, IV, V-Narrow Round and V-Wide Square roadway classifications available. Full-cutoff classification. Asymmetric option available with house-side shield. High impact resistant, injection molded clear textured UV-stabilized polycarbonate lens. 



Patent

U.S. Patent No. D707,387, U.S. Patent No. 8,810,137 B2.



Photometrics

Photometry tested to the IESNA LM-79-08 standard by an ILAC/ISO17025 accredited laboratory. For additional photometric data, please go to www.kenall.com.



TekLink TL1000/2000

An adaptive lighting control system with wired or wireless communication between system nodes. In addition to occupancy detection and daylight harvesting, TL1000 and TL2000 feature advanced scheduling and energy management capabilities with cloud-based management of system settings, reporting and notifications.




TekLink TL50

An independent lighting control system integral to the luminaire, featuring its own occupancy sensor, daylight harvesting and adjustable time-out/dimming settings.  



Warranty

Limited ten (10) year warranty. Polycarbonate lens required for Peace of Mind Guarantee®.