Technical Specifications


ELECTRICAL

LED array available in multiple CCT and CRI combinations with a maximum 3-step MacAdam variation allowance. See Trim Ordering Information for available options. 120-277VAC or 347VAC, 50/60Hz electrical input with serviceable constant current driver (0.90 PF). Minimum 85% driver efficiency. Standard 0-10V dimming with 1-100% range; 200µA max. source current. Optional DALI and Lutron EcoSystem dimming drivers with 1-100% range.


HEATSINK

Die-cast aluminum with external radial fins for natural convection.


INSTALLATION

Suitable for ambient temperature temperatures of -30oC to +40oC.


LISTINGS

Luminaire is certified to UL standards by Intertek Testing Laboratory for non-IC and Wet Location installations. IP64 and IP65 rating per IEC60598. NSF2 Splash/Non-Food Zone. Optional CCEA compliance.


OPTICAL

High-Efficiency mixing chamber design with regressed diffused tempered-glass lens producing uniform light output. Available with various reflector distribution patterns and finishes. Flush lens trim options include a clear lens. See distribution and reflector finish ordering information for available options.


PHOTOMETRICS

Photometry tested to the IESNA LM-79-08 standard by an ILAC/ISO17025 accredited laboratory.  For photometric information, go to www.kenall.com.


ROUGH-IN FRAME

18-gauge die-formed, corrosion-resistant steel. Vertically adjustable collar accommodates ceiling thicknesses up to 2", adjustable post-installation. Universal mounting brackets accept 3/4" and 1-1/2" lathers channel, 1/2" EMT conduit and hanger bars. Quick-access junction box accessible post-installation from above and below ceiling. Includes (4) 1/2" and (2) 3/4" knock-outs to allow straight conduit runs. Listed for (8) 12AWG, 90oC conductors and feed-thru branch wiring. Provided with FMC with electrical quick-connect to Trim Section.


TRIM/HOUSING SECTION

IP-rated housing section incorporates the heat sink, LED module, optics and lower trim.Configurable with an IP64-rated Regressed or Flush lens trim that is secured to the Rough-In frame with hidden torsion springs, and an IP65 Flush lens trim secured with four (4) Phillips-head, captive fasteners. See trim ordering information for available options.


WARRANTY

Five (5) year warranty against mechanical defects.  Five (5) year warranty on LED lamps and power regulation components for defects resulting in a fixture lumen depreciation of 30% or greater.